Place of Origin:
5hp Portable Water Chiller Air Cooled Cooler Chiller Air Cooling With Small Hermetic Scroll Compressor
Chiller which is also called water chiller units, industrial chiller, cooling system, cooling machine, cooling equipment, it offers chilled water with temperature from -40°C to +35°C and can be used for a variety of industrial and commercial applications.
Anges Chiller . Our industrial chiller adopts world famous brand components to ensure stable quality, high efficiency, energy saving and long service life.
Specification for Small Water Cooled Chiller System
|nominal cooling capacity||Kcal/h||14388|
|type of control||Capillary|
|compressor||type||Hermetic scroll type|
|condenser||type||Shell and tube|
|Cooling water flow(m3/h)||3.5|
|Inlet/outlet pipe caliber(inch)||1 1/2"|
|evaporator||type||Shell and tube|
|Chilled water flow(m3/h)||2.9|
|Inlet/outlet pipe chiller(inch)||1|
|Safety protection||compressor over temperature, over-current protection, high and low pressure protection, over -temperature protection ,flow switch protection,phase sequence or missing phase protection,exhaust overheating protection|
1. Famous brand belt compressor
Adopt famous brand compressor, low noise, low vibration, high efficiency and energy saving.
Shell and tube evaporator adopts high precision inner threaded copper tube design, which has larger heat transfer area, higher efficiency and maximum system performance.
Step 3: Water pump
Advanced stainless steel water pump, large working range, low noise, reliable performance, no leakage, maintenance free.
4. Microcomputer LCD controller
Cold water outlet and set temperature visual display, easy to operate, water temperature control in the range of 3℃~ 50℃.
Chiller daily maintenance
1. Before starting the compressor, check whether the pump rotates normally and ensure that the refrigerant in the pipeline system is fully filled and the circulation is normal.
2. To prevent the chiller from freezing, drain the refrigerant completely when it is not running for a long time. The automatic exhaust valve is installed at the highest point of the chilled water circulation pipe, and the drainage valve is installed at the lowest point of the chilled water circulation pipe.
3. The machine should be maintained by special personnel. According to the severity of the environment, the condenser of the air cooling unit should be cleaned once every 25 days, and the cooling tower pipe of the water cooling unit should be cleaned once every 2-3 months to ensure the heat dissipation effect.
4. The water quality shall meet the requirements in Appendix D of GB/T184330.1-2007. The pH of water should be between 6.5 and 8.0. The water should not contain Cl-, NH+, S² and other ions that are corrosive to copper. Install a filter in the inlet pipe and clean it regularly.
Send your inquiry directly to us