Place of Origin:
50 Ton Chiller Air Cooled Screw Chiller Process Chiller Central Chiller Cooling System Chiller Manufacturer
In an air-cooled chiller, hot refrigerant entering the copper tube fin condenser and it is exposed to atmospheric air, there's fan on top of the condenser for heat dissipation. The Air-cooled water chiller doesn't need cooling tower for operation, easier for installation and lower maintenance cost,due to no water treatment requirements. they are often a preferred choice especially in locations that water is shortage or very expensive.
Air- cooled Screw Chiller Specification
|nominal cooling capacity||kcal/h||141040|
|Max. Running current||A||127.6|
|type of control||thermostatic expansion valve|
|condenser||type||air cooled type finned copper tube|
|cooling air flow (m3/h)||51000|
|evaporator||type||shell and tube|
|chilled fluid flow (m3/h)||28.2|
|inlet and outlet pipe diameter (inch)||3|
|safety protection||compressor over temperature, unit overload, high and low pressure, flow switch, phase sequence, phase-missing, anti-freezing|
Screw Chiller Features:
Difference between screw chiller and scroll chiller
The two types of air cooled chillers are scroll compressor air cooled chillers and screw compressor air cooled chillers. Scroll compressors are used for the smaller air cooled chillers, and screw compressors are used for larger air cooled chillers and have a variable speed drive option for increased efficiency.
How to select the model of the chiller ?
Send your inquiry directly to us